The particle size produced by the Hydro SS averages 50 microns in size, with the probability of wetness below and near the unit. Particles measuring smaller than 50 microns will usually evaporate before hitting the floor. Mother nature’s fog averages 5 to 10 microns in size.
Suspending units up high and where no sensitive equipment is directly underneath is recommended. Maintaining drier floors can be enhanced by using an additional air moving fan to help evaporate the mist particles. Placing a fan directly underneath and aimed upward to blast air into the fog pattern will greatly increase and force evaporation, when necessary.
The optimal placement of the Hydro SS is high, overhead and oriented to propel fog in the direction of air flow.
The Bench Top should be placed at bench height or higher on a shelf. For the Direct Feed and Hanging Sump units, look for large, open areas up high. Allow adequate clearance directly in front of the fans, or objects that are too close could become wet and result in dripping. A Hydro SS aimed to propel fog horizontally will produce a downward arc in its fog pattern. Placing units higher allows more time for particles to evaporate as they fall, keeping floors drier.
Humidistat controls work best for applications requiring 80% RH or less. If you need to maintain RH above 85%, do not consider using a mechanical humidistat control.
If you are interested in evaporative cooling and have thermostatically controlled exhaust fans, using a humidistat control is a great choice. The two independent systems will work very well together, for cooling as well as for providing a maximum set point for relative humidity control.